The ever increasing global demand on the electrical energy has lead to the integration of Distributed Generators (DGs) onto the distribution power systems networks to supplement on the deficiencies on the electrical energy generation capacities. The high penetration levels of DGs on the electrical distribution networks experienced over the past decade calls for the grid operators to periodically and critically asses the impacts brought by the DGs on the distribution network operations. The assessment on the impacts brought by the DGs on the distribution network operations is done by simulating the dynamic response of the network to major disturbances occurring on the network like the faults once the DGs have been connected into it. Connection of Wind Turbine Generators (WTGs) into a conventional electrical energy distribution network has great impacts on the short circuit current levels experienced during a fault and also on the protective devices used in protecting the distribution network equipment namely; the transformers, the overhead distribution lines, the underground cables and the line compensators and the shunt capacitors commonly used/found on the relatively long rural distribution feeders. The main factors which contribute to the impacts brought by the WTGs integration onto a conventional distribution network are: The location of interconnecting the WTG/s into the distribution feeder; The size/s of the WTG/s in terms of their electrical wattage penetrating the distribution network; And the type of the WTG interfacing technology used labeled/classified as, Type I, Type II, Type III and Type IV WTGs. Even though transformers are the simplest and the most reliable devices in an electrical power system, transformer failures can occur due to internal or external conditions that make the transformer incapable of performing its proper functions. Appropriate transformer protection should be used with the objectives of protecting the electrical power system in case of a transformer failure and also to protect the transformer itself from the power system disturbances like the faults. This paper was to investigate the effects of integrating WTGs on a distribution transformer Fuse-Fuse conventional protection coordination scheme. The radial distribution feeder studied was the IEEE 13 node radial test feeder and it was simulated using the Electrical Transient Analysis Program (ETAP) software for distribution transformer Fuse-Fuse protection coordination analysis. The IEEE 13 Node radial test feeder In-line transformer studied is a three-phase step down transformer having a star solidly grounded primary winding supplied at and a star solidly grounded secondary winding feeding power at a voltage of . The increase on the short circuit currents at the In-line transformer nodes due to the WTG integration continuously reduces the time coordination margins between the upstream fuse F633 and the downstream fuse F634 used to protect the transformer.
Jim Pauley ‘’ Application of Over-Current Protection Rules to Transformers and Primary and Secondary Conductors’’ Codes and Standards Application Data. Square D Company. Bulletin Number 011DB0201. USA. Technical Report.
KP Kirui, DK Murage, PK Kihato: Impacts of Placement of Wind Turbine Generators with Different Interfacing Technologies on Radial Distribution Feeder Short Circuit Currents. Proceedings of sustainable research and innovation conference. JKUAT, ISSN: 2079-6226, Pg 206-212, 2020.
KP Kirui, DK Murage, PK Kihato: Impacts of Placement of Wind Turbine Generators with Different Interfacing Technologies on Radial Distribution Feeder Fuse-Fuse Protection Coordination Scheme. European Journal of Engineering Research and Science (EJERS), ISSN: 2506-8016, 4(10), Pg 59-77, 2019.
KP Kirui, DK Murage, PK Kihato: Impacts of Short Circuit on Wind Turbine Generator Interfaced Radial Distribution Feeder Sequence Impedances. Proceedings of sustainable research and innovation conference. JKUAT, ISSN: 2079-6226, Pg 250-255. 2019
Thomas P. Smith, “The ABC’s of Over-current Coordination- Analyzer” Published for electrical engineers by E POWER ENGINEERING. January 2006. Technical report.
Tasha Harvey “Selective Coordination for Over-Current Protective Devices: Application for Buildings in the United States” Kansas state university, master’s Thesis 2012.
EDWIN PHO “Over-current Coordination Study” California Polytechnic State University, 2009.
Square D “Guide to Power System Selective Coordination 600V and below” Schnelder electric 2006. Technical report.
Thomas Gallery, Laura Martinez and Danijela Klopotan “Impact of Distributed Generation on Distribution Network Protection” ESBI Engineering & Faculty Management, Ireland
W.H.Kersting “Radial Distribution Test Feeders” IEEE Power engineering society. Distribution systems analysis subcommittee report. 2000.
KP Kirui, DK Murage, PK Kihato: Fuse-Fuse Protection Coordination Scheme ETAP Model for IEEE 13 Node Radial Test Distribution Feeder. European Journal of Engineering Research and Science (EJERS), ISSN: 2506-8016, 4(9), Pg 224-234, 2019.
This work is licensed under a Creative Commons Attribution 4.0 International License.
The names and email addresses entered in this journal site will be used exclusively for the stated purposes of this journal and will not be made available for any other purpose or to any other party.
Submission of the manuscript represents that the manuscript has not been published previously and is not considered for publication elsewhere.